1 The AMF panel is used to monitor the EB Source and automatically Start/Stop the Genset. Also, The AMF
Panel execute the Change Over between EB Source and DG Source.
2 AMF Function through
1. AMF Relay
2. Line Voltage Monitor Relay
3 The AMF Relay has Protection like Voltage Monitor, Phase Sequence, Phase Loss, Phase Unbalance, Under Voltage & Over Voltage for both EB & DG. Also, It has the Protect the DG from Low LOP oil, Temperature & monitor the Battery voltage.
4 The Line Voltage Monitor relay monitors the EB Supply & Protect from Voltage Monitor, Phase Sequence, Phase Loss, Phase Unbalance, Under Voltage & Over Voltage.
5 Change Over Function
1. MCCB/MCB/SFU - Contactor combination
2. MCCB/MCB/SFU - Auto Transfer Switch combination
3. Motorised MCCB only.
4. Electrical Drawout ACB only.
6 Type Tested as per IS- 8623 and IEC 61439 –1&2 (Indoor & Outdoor)
7 Operational Voltage - 415 V, AC
8 Rated Insulation Voltage N- 1000 V, AC
9 Operational Current -Up To 1600A
10 Degree of Protection - IP –42 / IP –54 / IP -55
11 Short-circuit rating 50 / 65 kA.
12 Forms Seperation - 2a,2b,3a,3b,4a
13 Configuration - Fixed / Drawout
14 Complies with CEIG & CEA Regulations